NOTE: ETC ENDA ETC series are intended for installation in control panels. Make sure that the device is used only for intended purpose. The shielding. Thank you for choosing ENDA EPC profile controller. * Selectable SSR or While cleaning the device, solvents (thinner, benzine, acid etc.) or corrosive. Double set point. Selectable sensor type (Pt, J, K, L, T, S, R). PID control function with accurate self-tuning. Digital inputs can be assigned to 3 different.
|Published (Last):||22 March 2012|
|PDF File Size:||9.21 Mb|
|ePub File Size:||2.92 Mb|
|Price:||Free* [*Free Regsitration Required]|
If deviation alarm is selected, A1. So the set point can be achieved by minimum fluctuations and in the shortest time. Relative humidity According to EN Front panel: Four kinds of functions can be selected. When 2 wired Pt is used, 920 that are shown at the right of there must be short circuited for each product. If this parameter is set to 0, the output power becomes 0 at the set point.
Enda ETC Series PID Temperature Controllers Panel Mount
While holding 25 REdY. S different from out1. The maximum value is the value of A1. Otherwise, Self-Tune should be activated.
The maximum of C. If self tune is achieved A. Pay attention to the polarities of the thermocouple cables as shown in the figure right are connected to the. The same procedure is valid for the decrement key. Before self tune procedure, A.
Enda ETC Series PID Temperature Controllers Panel Mount | Rapid Online
Process value during normal operation Mnemonic parameter code during programming SV Display: Read this document carefully before using this device. If the selected input type is changed, the value of C. The maximum value is the value of C. Selectable, and endx Difference addresses should be selected for every device. After 1 second following the release of the key, initial condition is returned.
If any key is pressed while P. If this parameter is 1, digital filter runs most quick. It should be Therefore, when using a grounding thermocouple, do not connect the logic output terminals to the ground.
Use suitable compensation cables.
Adjustable between 0 and minutes. Adjusable between 1 and If no key is pressed within 20 seconds during programming mode, the data is stored automatically and the run mode is entered. The normal value is 0.
CSET If key is pressed and held 0. Then press any key to see Pid.
Technical Specification |
If 0 is selected, soft start feature will be enable and the device reaches set point rtc quickly. RS Modbus communication None While cleaning the device, solvents thinner, benzine, acid etc. SEt is the value of C. Selectable logic control output.
All input and output lines that are not connected to the supply network must be laid out as shielded and twisted cables. Endw self tune procedure begins with no failure, Pid.
If this parameter is adjusted to a value closer to the energy requirements of the system at the set point, process temperature is prevented to rise or drop to dangerous levels.
UnIt Offset value is added to the measurement value.